RCCB Earth Leakage Circuit Breakers (Residual Current Devices)
Earth Leakage is an electrical hazard and is responsible for electrical shocks and fire risk. Earth Leakage and its associated hazard can be prevented by residual current device (RCD), similar to that of a residual current circuit breaker (RCCB), also popularly known as Earth Leakage Circuit Breaker (ELCB). The products have been approved by CE/CB and SEMKO approval against standard IEC61008.
- CE/CB/SEMKO approval
- PMR and Core are made by ourself
- Simple and Robust operating mechanism.
- Rotary handle with ON/Off indication
- Dual termination for cable connection
- Advance Neautral
- Test Button for regular inspection
- OEM/ODM are welcome.
|Pole No.||2 Pole||4 Pole|
|Standard Conformity||IEC 61008-1||IEC 61008-1|
|Rated Current (In)||A||16, 25, 40, 63, 80, 100||16, 25, 40, 63, 80, 100|
|Sensitivity (In)||mA||30, 100, 300, 500||30, 100, 300, 500|
|Rated Voltage (Un)||Vac||240||240 / 415|
|Rated Insulation Voltage (Ui)||V||660||660|
|Shortcircuit Withstand Capacity||kA||6||6|
|Residual Making Breaking Capacity||A||10 In||10 In|
|Ambient Temperature||o C||-25 to +40||-25 to +40|
|Mounting||Din Rail (35 * 7.5) mm||Din Rail (35 * 7.5) mm|
|Degree of Protection||IP 20||IP 20|
|Terminal Capacity (max)||mm2||25||25|
- Thyristor/Diode Modules (Semiconductor Power Modules)
- Bridge Rectifiers
- Modular Contactors
- Proximity Sensor
The electromagnetic system adopts ...
It suits in three-phase AC 50Hz, rated ...
Export Markets: Global ...
It is ...
NSX moulded case circuit breaker ...
KNB6-63 High-breaking ...